Daily maintenance of fountain equipment in Chengdu
Publish Time：2020/12/29 News Number of views：312
Daily maintenance and reasonable construction of fountain equipment in Chengdu are equally important. Professional training is needed for fountain equipment maintenance personnel, and electrical equipment maintenance personnel also need to hold professional certificates. The fountain operators are assessed every six months to strengthen the use and management. Good engineering construction can ensure the good operation of the system, and reasonable maintenance can ensure the safety of the project, ensure the use, reduce faults, and avoid leakage and other dangerous accidents.
The installation of fountain equipment and the connection of fountain cable must be carried out without water, and three layers of waterproof tape, insulating tape and high voltage insulating tape shall be used for protection. The underwater lamp of fountain must be replaced under the condition of no water, and the bolts must be fastened firmly.
Chengdu fountain equipment inspection and underwater lamp inspection: the fountain underwater lamp shall be inspected and tightened once a month to avoid short circuit fault caused by water entering into the lamp body.
Inspection of cables: the cables laid in water shall be inspected once half a year to check the aging condition and avoid unnecessary loss.
Nozzle inspection: in order to ensure the beauty and consistency of the fountain water type, the nozzle with changing angle should be reset at any time. It is forbidden to use sharp objects to knock when resetting to prevent nozzle damage.
Inspection of fountain electrical equipment: the fountain electrical equipment shall be maintained regularly, and the vulnerable electrical equipment in the cabinet shall be inspected for half a year, and necessary maintenance shall be carried out; the maintenance and overhaul of electrical equipment shall be carried out under the condition of cutting off the power supply. If live working is required under special circumstances, safety protection measures shall be taken, and special personnel shall be assigned to monitor important parts.
Cleaning of Chengdu fountain equipment cleaning of fountain water pump: the water inlet of fountain water pump should be cleaned every month to prevent dirt from blocking the suction outlet, reduce work efficiency and even cause equipment damage. When the submersible pump is out of service in winter, the cooling water must be discharged to avoid freezing damage to the pump body, and the valve of the oil-cooled pump needs to be closed.
Fountain pipe cleaning: once a year. In winter, the water in the pipe should be drained before the fountain equipment is out of service to prevent the pipe from frost cracking.
Cleaning of fountain nozzle and underwater lamp: clean once half a year. Pay attention to the nozzle riser and underwater color lamp during cleaning to prevent damage.
The replacement of fountain equipment and standby equipment in Chengdu should be started and operated regularly (those with high usage frequency should be replaced every day, while those with low usage frequency should be replaced once a day), so as to prevent the performance of the equipment from declining. When replacing the diaphragm of the solenoid valve, all the objects falling off in the pipeline shall be cleaned up; when tightening the screws, they shall be carried out in diagonal order. Computers and programs are upgraded once a year.
- Fountain company to tell you what you need...
- How to choose Yunnan Music Fountain Company
- Design concept and cost calculation of fou...
- What are the commercial values of water sc...
- Let those colorful waterscape wake your ears.
- How many drainage systems are designed for...
- Invisible protection project of square fou...
- What details do you need to pay attention ...